Find the most up-to-date version of API RP 14F at Engineering The American Petroleum Institute’s Recommended Practice for Design and Installation of Electrical Systems for Offshore Petroleum Facilities, API RP 14F, un . Nov 5, For facilities classified as Zone 0, Zone 1, or Zone 2, reference API 14FZ, Recommended Practice for Design and Installation of Electrical.
|Published (Last):||12 February 2010|
|PDF File Size:||2.94 Mb|
|ePub File Size:||14.67 Mb|
|Price:||Free* [*Free Regsitration Required]|
If you wish to download it, please recommend it to your friends in any social system. Published by Nickolas Allan Jenkins Modified about 1 month ago. This document recommends minimum requirements and guidelines for the design and installation of new piping systems on production platforms located offshore.
Metal-clad cable as defined by NEC Aoi This document recommends minimum requirements and guidelines for the design apu installation of electrical systems on fixed and floating petroleum facilities located offshore.
30 CFR 250.114 – How must I install, maintain, and operate electrical equipment?
Applicable gas classification group s eg. This document recommends minimum requirements and guidelines for the design and installation of new piping systems on production platforms located offshore. The surrounding gas air mixture can automatically pai with out a spark being formed.
Mineral-insulated metal-sheathed cable as defined by NEC Article Applicable gas classification group s. This publication serves as a guide for those who are concerned with the design and construction of new platforms and for the relocation of existing platforms used for the drilling, development, and storage of hyd Inch, size or larger conduit run entering an enclosure that contains splices, taps, or terminals.
This Recommended Practice is intended to serve as a guide to crane owners and operators in developing operating and maintenance practices and procedures for use in the safe operation of pedestal-mounted revolving cranes on fixed or oating offshore platforms, jacku This is to provide a higher level of protection for their hazardous area equipment and personnel as they deem necessary.
Must be installed in and explosion proof container unless the certificate states otherwise. If Associate Apparatus is placed in the classified area then it must have another ai of protection. Why is it NOT acceptable? These advantages may include reduced initial capital expenditures, enhanced safety, or facilities that are more easily and more economically maintained.
As tested by the NFPA This document is intended to bring together in a;i place a brief description of basic desirable electrical practices for offshore electrical systems. The classified areas are different and some protection concepts also differ.
API RP 14FZ PDF
Zone 2- Not likely or normally confined in containers. The practitioner should in all cases seek full and proper guidance from the relevant legislation and codes aapi practice in addition to following company guidelines and procedures. This recommended practice is intended to assist in development of a management program designed to promote safety and environmental protection during the performance of offshore oil and gas and sulphur operations.
Ro basic function of a FPS is to receive hydrocarbons from the wellhead, process the hydrocarbons, and store Explosion proof equipment may not provide protection against the ingress of liquids or solids therefore, breathers and drains may be 1f. Type PLTC nonmetallic-sheathed, power-limited tray cable.
This recommended practice is intended to assist in development of a management program designed to promote safety and environmental protection during the performance of offshore oil and gas aip sulphur operations.
Zone 1 Equipment must be certified as meeting the requirements of the area this could be a number of different protection concepts not just Flame-Proof. Regulators such as U. This recommended practice covers methods 14v installation for pressure-relief devices for equipment that has a maximum allowable working pressure MAWP of 15 psig 1.
Associated Apparatus Is apparatus that not all the circuits are intrinsically safe. Must provide adequately maintained breathers and drains to prevent accumulation of moisture This document provides guidelines and recommended practice for the satisfactory design of offshore structures against fire and blast loading.
This document provides guidelines and recommended practice for the satisfactory ap of offshore structures against fire and blast loading.
This equipment has additional security against the possibility of excessive temperature and the equipment is assembled very carefully to ensure that arcing or sparking from part to part or connection to connection will not occur.
C aapi Sparking equipment in which the contacts are suitably protected other than by restricted breathing. This document recommends minimum requirements and guidelines for the design, installation, and maintenance of electrical systems on fixed and floating petroleum 14d located offshore.
API RP 14F: Recommended Practice for Design and Installation of
Disconnect switches in general purpose enclosures should not be used offshore in classified locations; this is a departure from the NEC. This ensures that apu gas or vapor located above the arcing or sparking parts or the gas or vapor located exterior apu the enclosure cannot be ignited by the electrical xpi parts apl the oil. Sealing accomplished by fusion of metal to metal or sealed through glass to metal. Grounding of electrical equipment on fixed and floating offshore petroleum facilities in a positive manner is of particular importance because personnel standing on steel decks or in contact with steel framing present a low impedance path to ground, effectively grounded For sizing equipment grounding conductors, refer to NEC Table.
Providing protection from fire, smoke, water and blast pressures. Its only intrinsically safe when employed in a properly designed intrinsically safe circuit.
Metal-clad cable for hazardous locations as defined in UL MI cable: Markings on the equipment to ensure the correct location of installation are as follows; Zone Equipment. This document recommends aapi requirements and guidelines for the design and installation of electrical systems on fixed and floating petroleum facilities located offshore when hazardous locations are classified as Zone 0, Zone 1, or Zone 2. OK Forward looking statement.
Medias this blog was made to help people to easily download or read Ep files. Energy Limited nL Limit energy of sparks; wpi the temperature of a device replaced by Ex ic. Strict rules must be followed, system calculated to ensure energy aoi are within tolerances and diagrams must be followed closely as wells as the current RP, Codes and Standards.
This recommended practice covers methods of installation for wpi devices for equipment that has a maximum allowable working pressure MAWP of 15 psig 1. All seals should be installed as close as practicable, ai in no case more than 18 inches, from the enclosures to which they are attached. Thus, the protection techniques for equipment to be installed in Zone 1 locations can be less demanding than the protection techniques for equipment to be installed in Division 1 locations.