Part of the BACHARACH family of products. HGM / RDM Refrigerant Gas. Monitoring System. Refrigerant Gas Detection,. Identification & Monitoring. Refrigerant monitoring system • Read online or download PDF • Bacharach HGM User Manual. View and Download Bacharach HGM installation, operation & maintenance instructions manual online. Refrigerant Gas Monitoring System. HGM
|Country:||Sao Tome and Principe|
|Published (Last):||26 April 2012|
|PDF File Size:||20.77 Mb|
|ePub File Size:||6.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Table of Contents Add to my manuals Add.
This is the correct setting if the HGM is connected hgm3300 a single device, or it is the last device on the network chain. All pending alarms across the entire bacharacu must be acknowledged before the RDM returns to normal operation.
Alarm Detail Screen The Alarm Detail Screen displays more comprehensive information about the nature of the alarm including: The monitor should be installed out of direct sunlight in a clean, dry area that is not subject to temperature or humidity extremes. DO NOT use soap and water. RDM – Screen Displays When first powered up a splash screen appears indicating the serial number and firmware revision number.
Yokogawa HGM Halogen Gas Monitor Hgm Bacharach VAC | eBay
Combustion analyzer standard efficiency equations, siegert efficiency equations, and nsx version 87 pages. Page 67 Programming New Gasses As new refrigerants come into use the HGM allows the addition of these new gases to its on-board refrigerant gas library.
Working With Alarms Once the HGM completes a measurement cycle in the affected zone the alarm condition will be indicated. The first register contains bytes and the second register contains bytes. Once jgm300 blockage has been cleared, the HGM will return to normal operation after the zone has been sampled.
An exhaust line is installed to vent residual gas away from the monitor.
The HGM should be centrally located in the mechanical room and be readily accessible for easy visual monitoring and servicing. For example, at the default scale factor of 0. This manual also for: Location This is the name you assign to the HGM to identify its location.
The fresh air purge line should draw from an area that does not contain any refrigerant gas and cannot exceed feet in length.
Appendix Appendix Instruction The boxes on the left side of the screen indicate the status of each HGM monitor including the name, the current zone, and bscharach fault or alarm conditions are present on the network. Use any of the remaining service knockouts to gain access to the interior of the monitor. In order to place the HGM into service mode use the following sequence: Comments to this Manuals Your Name.
It may have up to 12 alphanumeric characters. The second is a PPM reading normalized to standard temperature and pressure. There are two versions of PC software.
The default value is feet. Average Temperature This temperature reading may be changed to the exact temperature at the sample point for bahcarach accuracy.
Yokogawa HGM300 Halogen Gas Monitor Hgm-300 Bacharach 120 VAC
To print the manual completely, please, download it. Page 50 Average Temperature This temperature reading may be changed to the exact temperature at the sample point for greater accuracy. Zone Hold Mode A zone can be placed on hold and continuously monitored for a hgm30 of time determined by the Zone Hold Time value Page Press the adjacent key to adjust the setting. To place a zone on hold, press and hold down the key adjacent to that zone until bacharacg hear a beep.
If you are unfamiliar with this information, please reference the HGM operations manual.
Bacharach HGM User Manual | 26 pages
Use any of the remaining service knockouts to gain access to the interior of the RDM Don’t have an account? This value must be less than the evacuate level and greater than the leak level. Warning Statements Safety Precautions Cont. Service Pursuant to the stated warranty, Bacharach, Inc.